CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. 1 SCOPE This Standard prescribes requirements for the inspection and testing of fire alarm systems and specifies the devices and functions.
|Country:||United Arab Emirates|
|Published (Last):||17 February 2004|
|PDF File Size:||10.44 Mb|
|ePub File Size:||8.17 Mb|
|Price:||Free* [*Free Regsitration Required]|
Ancillary devices, which are powered from the control unit or transponder, are recorded.
Plugging of sprinklers found during activation or alteration? Most smoke detectors installed today are wired directly to the household electrical system.
S Input circuit supervision fault causes a trouble indication. Where active and supporting field devices are utilized, device labels correspond with actual field location. If housing discolouration is noted, attempt to identify the source and note the date of manufacture.
Alarm signal silence visual indication hlc Alarm signal and visible signal devices, when silenced, automatically reinitiate upon O subsequent alarm.
Exceptions are identified in the Device Test Record. P Emergency telephone operable or in-use tone at handset operates. Photoelectric type smoke detectors utilize an infrared light source called the emitter and a receiver, both of which are located inside the sensing chamber. Clean Cloudy Dirty Inspect duct work for combustion air? The fire signal receiving centre ULC certification number is: Fire Safety and Emergency Planning. Batteries 2 voltage readings are normal Check accuracy of pressure gauges and sensors?
Record of broken mains in the vicinity? This form is intended to provide the owner or fire inspector with an overview of what fire protection systems exist in the building and which systems were inspected and tested by a qualified technician. Operates on emergency power.
Standards Council of Canada
Battery Capacity as installed: Applying household voltage to the interconnection wire will dan in the destruction of any connected alarms and may even cause a fire. Ancillary functions visual indicators operates. Indicate type of test performed on a fully charged battery select one: Remote trouble signal unit identification: Confirmation of wiring supervision and ground fault indication is required to be carried out at all end-of-line devices on s53 annual basis.
H Operation of voice paging does not interfere with initial inhibit time of alert I signal and alarm signal.
D B Terminal connections clean? Oil level in normal check sight glass Wet pit suction screens are unobstructed and properly installed Condition of oil in sight glass? There is fire protection equipment located at the above referenced address that has not been tested in accordance with the NO Provincial Fire Code. Minor leak at no flow?
Fire Alarm System Periodic Inspection (CAN/ULC-S)
C F Discharge pressure at gauge: Will racks swing out of the cabinet at least ninety 90 degrees? Your service agency MUST identify those detectors that it could not perform this test on. Alarm valves shall be inspected externally. These units are vulnerable to electrical failures they won’t function in the absence of power. Refer to Appendix F2 ; iv A battery capacity meter test.
CAN/ULC-S536-04 Fire Alarm Annual Inspection Test Form
Cabinets easy to fully open? Audibility of alarm sounder checked? F Confirm that the alarm transmission to the fire signal receiving centre is received.