test code for step-voltage regulators. IEC , Insulated bushings for alternating voltages above 1 V. IEC , Tap-changers – Part 2. This part of IEC is intended to assist in the selection of tap-changers designed in accordance with IEC or IEEE Std. C for use in. Tap-changers –. Part 2: Application guide. Reference number. IEC (E). This is a free 6 page sample. Access the full version online.
|Published (Last):||12 September 2011|
|PDF File Size:||1.41 Mb|
|ePub File Size:||1.4 Mb|
|Price:||Free* [*Free Regsitration Required]|
From Wikipedia, the free encyclopedia. In other projects Wikimedia Commons.
If you need help with the purchase or have any queries please email enquiries standards. They are often more costly but this method is used in some modern transformers. International Classification for Standards ICS is an international classification system for technical standards.
Safety of power transformers, power supply units and similar – Particular requirements – Particular requirements for isolating transformers and power supply units incorporating isolating transformers You may be interested in this related standard Safety of transformers, reactors, power supply units and similar products for supply voltages up to 1 V — Part 2. It is designed to cover every economic sector and virtually every activity of the humankind where technical standards may be used.
Siemens — via http: Thyristor-assisted tap changers use thyristors to take the on load current while the main contacts change over from one tap to the next. This article includes a list of referencesbut its sources remain unclear because it has insufficient inline citations.
iwc Also called On Circuit Tap Changerin applications where a supply interruption 602144-2 a tap change is unacceptable, the transformer is often fitted with a more expensive and complex on load tap changing mechanism. It commences operation at tap position 2, with load supplied directly via the right hand connection.
All of the winding taps will then be routed into the tap changer compartment through a terminal array. A mechanical tap changer physically makes the new connection before releasing the iecc using multiple tap selector switches but avoids creating high circulating currents by using a diverter switch to temporarily place a large diverter impedance in series with the short-circuited turns.
Application guide This document has been re-assessed by the committee, and judged to still be up to date.
Tap changer – Wikipedia
No load tap changers are also employed in high voltage distribution-type transformers in which the system includes a no load tap changer on the primary winding to accommodate transmission system variations within a narrow band around the nominal rating.
The low voltage tap may be requested to change positions multiple times each day, without interrupting the power delivery, to follow loading conditions on the low-voltage secondary winding network. The high voltage tap is set to match long term system profile on the high voltage network typically supply voltage averages and is rarely changed. This power consumption can add up to a few kilowatts which appears as heat and causes a reduction in overall efficiency of the transformer; however, it results in a more compact design that reduces the size and weight of the tap changer device.
Standards New Zealand :: Tap-changers – Part 2: Application guide
During a tap change operation, the potential rapidly increases between the two electrodes in the bottle, and some of the energy is dissipated in an arc discharge through the bottle instead of flashing across the diverter switch contacts. This technique overcomes the problems with open or short circuit ic.
Retrieved from ” https: The result operates like a dual-clutch transmissionwith the tap selector switches taking the place of the gearbox and the diverter switch taking the place of the clutch.
Alternatively, in some systems, the process of tap changing may be assisted by means of a rotary or slider switch.
Diverter resistor A is short-circuited; diverter B is unused. Automatic tap changers can be placed on a lower or higher voltage winding, but for high-power generation and transmission applications, automatic tap changers are often placed on the higher voltage lower current transformer winding for easy access and to minimize the current load during operation.
In such systems, the tap changer will often be set just once, at the time of installation, although it may be changed later to accommodate a long-term change in the system voltage profile. On load tap changers may be generally classified as either mechanical, electronically assisted, or fully electronic.
This type of transformer is frequently employed in low power, low voltage transformers in which the tap point often may take the form of a transformer connection terminal, requiring the input line to be disconnected by hand and connected to the new terminal. Tap changers typically use numerous tap selector switches which may not be switched under load, broken into even and odd banks, and switch between the banks with a heavy-duty diverter switch which can switch between them under load.
Articles lacking in-text citations from September All articles lacking in-text citations Commons category link is on Wikidata. We recommend that you check the website of the publishers of the international document before making a purchase. Agbioeletric Balun Buchholz relay Bushing Center tap Circle diagram Condition monitoring of transformers Copper loss Dissolved gas analysis Electrical insulation paper Growler High-leg delta Induction regulator Leakage inductance Magnet wire Metadyne Open-circuit test Polarity Polychlorinated biphenyl Quadrature booster Resolver Resonant inductive coupling Severity factor Short-circuit test Stacking factor Synchro Tap changer Toroidal inductors and transformers Transformer oil Transformer oil testing Transformer utilization factor Vector group.
Also assists in understanding the various types of tap-changers and their associated equipment available. If only one tap changer is required, manually operated tap points are usually made on the high voltage primary or lower current winding of the transformer to minimize the current handling requirements of the contacts.
The tap selection on any tap changer oec be made via an automatic system, as is often the case for OLTC, or a manual tap changer, which is more common for NLTC.